You can view the PDF files conveniently online with your browser – just click the link. Alternatively, you can save the information so that you can refer to it offline. Find out all of the information about the FRAKO product: power factor control relay / panel-mount / programmable / digital RM Contact a supplier or the. (see Table 1, pages 15 to 17) The Reactive Power Control Relay RM is Relay RM Sales Programme Power capacitors for low voltage FRAKO.
|Published (Last):||16 May 2012|
|PDF File Size:||13.78 Mb|
|ePub File Size:||20.42 Mb|
|Price:||Free* [*Free Regsitration Required]|
The current transformer can be installed in any phase. If this ratio is exceeded by the factor set for at least one minute due to harmonics and the resulting resonance phenomenon, the control relay switches off all stages which have been switched on.
If the set mode has been activated within these 5 minutes, it remains available for one hour.
By pressing the “Set” button the display shows the maximum value of the factor by which the RMS current has exceeded the nominal current. Switched off -3 -2 cap Reactive current Switched on 1 -1 One scale division corresponds to 0.
When the optional switching combinations are sorted according to their capacity, the capacity difference between two successive combinations may only be 1.
The size of the capacitor stages has no influence on this setting. Refer to section 2.
At a well laid out spacious factory at Chennai, Power quality systems are manufactured with stringent quality tests to maintain the high performance systems of Baron. Should the control relay fail to identify the current and voltage source due to power instabilities, repeat the procedure when the power has stabilized.
Used Frako RM Trafostation for Sale (Trading Premium)
The discharge period, which ensures that the capacitors are fully discharged before they are switched on again, overrides the switching delay time see section 5. The “kink” in the band characteristic line fraako not reflected in the feedback operation but is extended at the point of intersection of the reactive power centre line axis with the feed-back operation line.
Unstable power supply power factor fluctuation.
By pressing the “-” button once “6. If the identification process is not concluded within 15 minutes there is probably a fault. Faults 8 9 10 11 Despite inductive load no stages are switched on when relay is in automatic mode.
In the second line above a more accurate result can be achieved with the same number of switching contactors. Store this value by pressing the “Set” button. Plug-in connector blocks supplied with the control relay Zero Current Trip: Measure the frwko of each capacitor stage with a clamp-on current meter. The switching sequence does not take into account the fixed stages.
It will shift to the inductive direction if the plus sign is used and to the capacitive direction if the minus sign is used. An appropriate combination of “parallel shift” and “limitation” is illustrated in Figure 9. Reactive current Figure 8: Use ammeter to check current on secondary side of CT. Product Description The reactive power control relay RM is a microprocessor-based control relay for fraako control of capacitor banks with ffrako control contacts.
If this, however, is not possible due to lack of capacitor stages available, an alarm is signalised after several ffrako depending on the size of the difference. If measurements are not carried out via a summation transformer, the current change, measured by the control relay, is too low when switching on the capacitor stages, which can lead to errors during the automatic stage identification process.
If the CT ratio is programmed into frakko relay, the actual active current is displayed; otherwise the current portion is displayed and must be multiplied by 96606 CT ratio to obtain the actual value.
FRAKO RM Reactive Power Control Relay | eBay
If this cannot be achieved grako voltage must be earthed, even if it is only small protective voltage. In the case of the correct operating voltage, the contact closes if there is an alarm.
If the 6th stage was already switched on “6. All other stages follow according to their capacity. Current transformer circuit interrupted or there is no current flowing on the secondary side. Before a reactive power control system can be put into operation, the target power factor has to be programmed. Check the control circuit according to the circuit feako and repeat the automatic test procedure.
All information on FRAKO
Preset up to three fixed capacitor stages which will be 96006 from normal automatic operation. The rated current in the current transformer path should not exceed 5 Amps. Fraio relay does not switch off all stages during times of low load Control relay is in manual or facility shut-down.
The result corresponds to the connection mode number which have to be entered. Suitable for current transformers 96606 rated secondary current of 1A or 5A. Get best deals for coconut. This means that even when active power feako fed back into the mains, the control relay ensures compensation for the reactive power which has been drawn from the mains. Relay does not respond to manual operation although it has voltage and digital display is operational. If a capacitor stage is added later on, or defective fuses are exchanged, the RM itself identifies this after some time and the stage is then reintegrated into the normal operation.
If there is an interruption in the measurement voltage path, the control relay switches off all stages after about 1 sec. Find more suppliers in Chennai Power Controllers rfako Chennai. Check the control circuit according to the circuit diagram and check fuses. The effects are illustrated by the two examples in Figure 6 and Figure 7.
In case of low voltage networks being fed by several transformers switched in parallel, the capacitor current is distributed to all the transformers.
The control relay must be kept voltage free during wiring and installation works. The LED “Regen” indicates that generative active power is fed back into crako mains.